Monoblock plants – BIOTAL wastewater treatment
|Basic plant, made of polypropylene with dehydration unit |
|MCW-R ||Basic plant with box-recuperator |
|Basic plant with box-recuperator and biological filter |
|Basic plant with biological filter |
|MCW-BU ||Basic plant with biological filter and UV disinfection unit |
|Basic plant with biological filter, box-recuperator and UV disinfection unit |
Monoblock plants of the type (BIOTAL-MCW) are designed for deep biological treatment of household wastewater from 1.5 to 12 m3/day. A feature of this type of monoblock plant is that the excess active sludge is pumped into a separate well, where the stabilization and compaction processes take place.
Cylindrical polypropylene bioreactor, divided into cleaning zones, is located in an underground ferro-concrete well at a distance of at least 5 m from the residential building. The annular gap between the walls of the plant and the wall of the well, after filling the unit with water, is filled with a cement-sand mixture layer by layer, with “soaking” the water. With gravity flow of sewage to the plant, the marking of the bottom of the wells is determined based on the mark of the bottom of the supply pipeline. The automatic control unit of the BIOTAL plant and the blower can be installed in an existing non-residential heated room equipped with ventilation, a specially constructed blower building or in a box-recuperator that is installed in the well ceiling. Cables and air ducts must be laid in protective cases. The maximum distance from the plant to the blower building is 20 meters. The drainage of treated sewage is possible by gravity or by a pump installed in the tertiary settler of the plant.
Please note! The warranty period for BIOTAL plants is 5 years, for the control unit and blowers – 3 years, for pumping equipment – 2 years.
Service maintenance of monobloc installation BIOTAL we recommend to conduct: for private sector objects (cottages, private and country houses, mansions …) – once a quarter, and for other types of objects (gas stations, cafes, hotels, production .. .) – 1 time per month. ”
- Stainless grid for coarse impurities detention
Detention of coarse impurities at the BIOTAL plant takes place in a large stainless grid with two-sided air bubbling and a fixed cover.
- Siphon airlift
A device designed to transfer treated sewage into a biofilter-tertiary settler, the design of which prevents entering of surface contaminants to the next cleaning zone.
- Biological filter
Self-cleaning biological filter provides post-treatment of waste water, and also works as a thin-layer settler.
- Water level sensor
Is designed for the timely delivery of signals to the automation of the plant, which in turn automatically switches the system into one of 7 programs, which saves up to 70% of electricity.
- UV disinfection
The ultraviolet water disinfection unit is equipped with a lamp with radiation in the UV-C range with a wavelength of 254 nm.
The aerator is made of PUR membrane with laser perforation, provides small-bubble aeration of waste water, which allows to increase the efficiency of saturation of sewage with oxygen, and also improves the absorption properties of bacteria of activated sludge.